Important Safety Recommendations: NFPA 70E
NFPA 70E Article 120 Establish an "electrically safe work condition" before working on a circuit by deenergizing it.
Create an "electrically safe work condition" by… *
(1) Identifying all power sources,
(2) Interrupting the load and disconnecting power,
(3) Visually verifying that a disconnect has opened the circuit,
(4) Locking out and tagging the circuit,
(5) Testing for voltage, and
(6) Grounding all power conductors. (used for stored or induced electrical energy and bare-hand work)
*All of these steps require the use of appropriate personnel protective equipment for shock and arc flash protection: safety glasses, voltage rated gloves, fire–resistant (FR) work clothes, arc–rated face shields, flash suits with hoods, and hearing protection.
Energy Control and Power Lockout ECPL
Whenever a worker has to be placed in a position where a part of their body may be exposed to unexpected movement, release of stored energy, electrical system energizing or potential of exposure to the flow of liquids or gasses, they have the authorization and responsibility to effectively de-energize the machinery or equipment to prevent injury or death.
Before working on any machine or equipment, it is imperative that while it is being serviced to first remove its source of electrical power. The removal of all energy sources by disconnecting and making equipment safe (inoperable) is known as energy isolation. The procedure for shutting off the power and preventing it from being energized while the work is being done is called Lockout/Tagout. This de-energized state is also referred to as creating an electrically safe work condition, abbreviated as "ESWC".
Locking out and tagging equipment does not guarantee the electrical hazards have been eliminated until the equipment is verified as being in an de-energized state. Workers must continue to perform energized electrical equipment safety practices and wear PPE appropriate for the level of incident energy until the "ESWC" is established.
OSHA 1910.147(b) defines an energy source as "Any source of electrical, mechanical, hydraulic, pneumatic, chemical, thermal, or other energy."
It is important that you know each of the OSHA recommended 8 steps for lockout/tagout in proper sequence and that you know that each person who works on equipment should have his or her own lock for preventing a piece of equipment from being started inadvertently. See OSHA's 1910.147(c)(4) Energy control procedure and 1910.147 App A . Typical minimal lockout procedures.
Click on the link below to read OSHA requirements for lockout/tagout:
Clicking the link will open a new browser window. Close the new window to return to this lesson.
NOTE: Every facility or plant will have its own machine and equipment lockout/tagout standards and which must be followed at all times.
Figure 1: Energy Control Power Lockout
Figure 2: OSHA 8-Step Sequence of Lockout and